DCA Report Format
Included in our report would be a gap style analysis comparing your existing facilities attributes to those expected in best practice standards. Specifically we would use standards developed by the Uptime Institute and referred to as the 4 Tier Levels.
One of the components of the report would be a rack level “Electrical GRID Audit” to ensure consistent and effective connection of all IT loads in the proper 2N manner. (i.e. ensuring that all dual corded IT loads are properly connected to the sites respective power sources). The “GRID Audit” would provide a “rack-by-rack” review of all power cords feeding all dual corded and single corded IT loads, and provide step-by-step remedial recommendations.
The study would also provide a comprehensive prioritised list of recommendations in order to make your data centre facility meet best practice standards. Cost estimates would also be provided with the recommendation list in order to start with budgeting exercises and financial planning.
The DCA Report
We have outlined the general format of the report. It would include these sections dealing with the following elements:
1. Site Overview
The site overview would provide you with a detailed description of the site, it’s function, and the support systems found within it.
2. Current Status Drawings (AutoCAD Format)
Drawings (AutoCAD format) would be prepared to reflect the current status (as built) of the site (i.e. Electronic Environment area). The drawings would include (limited to):
- Architectural (rooms, walls, partitions, etc.)
- Equipment Layout (hardware location – IT and support systems)
- Electrical (single line and layout)
- Mechanical (single line and layout)
- Fire Suppression (single line and layout)
3. Hardware Inventory and Loading Estimates
This section would assess the existing loading (electrical and mechanical) of each functional area (i.e. network area, server area, etc.) and provide estimates for future growth potential. This section will also collect all pertinent information (which is presently being compiled by others), with regards to the following related items:
- Computer hardware inventory list (by room and functional area basis)
- Electrical support systems hardware inventory list (including technical specifications)
- Mechanical support systems hardware inventory list (including technical specifications)
4. Support Systems Review and Audit (Electrical and Mechanical)
Generally, the two main critical environment support systems are comprised of both electrical and mechanical elements. We will provide analysis of the facility’s electrical and mechanical systems, in order to properly assess present condition, total capacity, and present level of reliability.
For the electrical distribution system, we will provide load testing (capacity) and power quality analysis at the major distribution point(s) affecting the critical area.
The test performed on the electrical system will also attempt to quantify and isolate potential sources of electrical power problems. We shall provide a detailed description of the suspected and/or problem causing agents, and provide specific recommendations and instructions for remedial action (if/as required). Measurements and investigations will be performed at appropriate locations within the facility. Special attention will be provided to specific areas of interest that have been identified as the data center’s mission critical areas.
- Under floor Raised Floor Area – Electrical distribution review
The study will also include the proper identification of all electrical cabling and circuitry, located under the raised floor area (and or within the critical environment). All power cables and receptacles will be identified and labeled by tracing and identifying their point of distribution (i.e. panel boards and circuit breakers).
All circuit breakers at load centers will be properly traced, identified, and labeled for circuit identification. An “as-built” single line electrical drawing will be completed. All unused and/or abandoned cables will be identified for removal.
- Life Cycle Analysis (Support System Upgrade Strategy)
Based on our analysis of the site, we will provide you with an efficient and cost effective support system hardware upgrade and replacement strategy as/if required (i.e. mechanical and electrical systems, etc.). This plan will deal specifically with the data center support hardware which will include your electrical distribution system (i.e. UPS system, batteries, generator, etc.) and mechanical systems (i.e. air conditioners, etc.).
- Long Term Growth Strategy
A proposed long-term growth strategy would look at the present status of the data center (existing features, etc.) and would provide a basic plan for efficient future growth based on both the facility’s existing and/or future capabilities.
- Site Enhancement Recommendations
Based on the findings of the report, we will provide recommendations for site enhancement and improvement as/if necessary. The recommendation list will take the form of a prioritized “TO-DO” list that will provide you with the basis for immediate and effective site maintenance and management.
Synergy Data Centres is pleased to announce the appointment of Jacquelin Hodgson as Synergy Data Centres’ new Project and Service Manager. Please feel free to contact Jacquelin for all you service inquiries. She can...Read More
Synergy Data Centres will soon be one of Schneider’s newest EcoXpert Partners. Schneider Electric will leverage Synergy’s, well established existing Power Quality Consulting service (est. 1993 – PowerCET Canada – Better Technologies) and it’s...Read More
Synergy is now APC/Schneider’s Exclusive Authorized Elite Software Partner in Eastern Ontario and can provide full support for your StruxureWare based monitoring systems. After strict training at the APC/Schneider factory, Synergy is now an...Read More
Our Best Practices data centre demo centre is now complete and ready for your enjoyment. It would be our pleasure to give you a tour of our facility where you can see a complete,...Read More
Our new Technology Demonstration and Training Centre is almost completed. We are expecting to be up and running by September 31st 2014.Read More
APC’s new second generation HACS is now available. With features like, sliding doors, integrated hot aisle LED lighting, adaptable height ceiling panels, and enhance multivendor rack compatibility. On display now at our technology demonstration...Read More
A big welcome to Synergy’s new Sales Manager – Ross Macklem. Ross has over twenty years of experience in our field and will be a huge asset to our sales efforts. We received glowing...Read More
A new market trend has recently emerged with regards to “grading and certifying” data centre quality with the use of the “Tier Level” standard developed by “The Uptime Institute”. With over 20 years in...Read More
Synergy’s New Training and Demonstration Centre is soon to open its doors. The Centre will have a state of the art training facility as well as a fully operational demonstration area. Our demo area will...Read More